Appliances deionization water of removing more than 99.5% of salts are dissolved in water supply. The outlet (exit) device (column) provides high quality deionized water, conductivity of 10 mS / cm.
2. PHYSICAL PROPERTIES
Devices (batteries) containing a mixture of ion exchangers deionization resins specially formulated, capable to hold all the chemical species of cations and anions to form salts that are dissolved in water.
The new and unsaturated resin is 100% ready to apionisei water and is colored bright blue-green colored. The old and saturated resin, which is charged with salt, pale yellow in color. The old resin has potential for further deionization column and needs replacing.
The column operates in a vertical position JIA maximum efficiency. The point at which it is to be protected from direct sunlight and the temperature is minimum and maximum 5οC and 30 ° C. and respectively.
The maximum flow output of the device in deionized water without negatively influenced the quality is 600 liters per hour.
> To start the column must not open the valve abruptly but gradually.
> For the longevity the proposed provision should not exceed 200 lt / hr.
> The flow of water headers are strictly from top to bottom.
> After exiting the device must be placed no valve, but the flow is completely free.
The column in the operation of koregnytai gradually salts. Visually it seems to change the color of the resin from the top of the party, which gradually extends downward until it occupied the entire amount. From this point, then the device can no longer give out the water with the expected quality and requires replacement.
Replacing the saturated device is immediately on the telephone and personal contact with our company.
6. COLUMN TYPES
DIMENSIONS (DxH) mm
(Inlet water total hardness 20οF)